In every Class B institutional unit as defined in Sections13-56-050" destination-id="JD_13-56-050">13-56-050 and 13-56-060" destination-id="JD_13-56-060">13-56-060 and in every Class C assembly unit as defined in Section 13-56-070" destination-id="JD_13-56-070">13-56-070, not less than one approved carbon monoxide detector shall be installed per every 10,000 square feet, or fraction thereof, (a) on every floor on which a fossil fuel-burning appliance, boiler or furnace is located, and (b) on every floor heated by any type of warm air heating plant as defined in Chapter 13-184* that burns fossil fuel. On every floor of a Class B institutional unit which contains sleeping quarters, one approved carbon monoxide detector shall also be installed within 15 feet of all rooms used for sleeping purposes that are either (a) located near a fossil fuel burning appliance, boiler or furnace or (b) heated by any type of warm air heating plant, as defined in chapter 13-184, which burns fossil fuel. Floor area shall be computed separately for each floor.
(Added Coun. J. 3-23-94, p. 47711; Amend Coun. J. 3-6-96, p. 17599, effective 10-1-96; Amend Coun. J. 7-31-96, p. 26646, § 1; Amend Coun. J. 3-14-07, p. 99609, § 1)
* Editor’s note – Coun. J. 7-9-03, p. 3609, § 1, repealed Ch.13-184, which pertained to warm air heating plants.