Not less than one approved smoke detector shall be installed in every single-family residential unit and multiple dwelling units as defined in Chapter 13-56, Sections 13-56-020, 13-56-030 and 13-56-040. The detector shall be installed on the ceiling and at least four inches from any wall or on a wall located from four to 12 inches from the ceiling, and within 15 feet of all rooms used for sleeping purposes, with not less than one detector per level, containing a habitable room or unenclosed heating plant.
(Prior code § 52-11.1; Amend Coun. J. 4-25-84, p. 6189; Amend Coun. J. 9-8-86, p. 33588)